WTSML Heat Transfer Technology Co.,Ltd
Add: Qiaoxing Road 150, Torch Industrial Zone, Licheng Area, Quanzhou, Fujian, China
Tel:86 595 22168106
Fax:86 595 22142090
Heat exchanger pressure test
(1) The fixed tube sheet heat exchanger performs the shell side pressure test first , and at the same time checks the heat exchange tube and the tube sheet joint joint, and then performs the tube test pressure;
(2) U-tube heat exchanger, kettle type reboiler (U-shaped tube bundle) and stuffing-type heat exchanger use the test pressure ring for shell-side pressure test first ,at the same time check the joint, and then carry out tube test;
(3) The floating head heat exchanger and the kettle type reboiler (floating head type tube bundle) use the test pressure ring and the floating head special tool for the tube head pressure test first, and the kettle type reboiler should also be equipped with the special case tube head pressure test . Then, the tube test is performed, and finally the shell test is performed;
(4) The pressure test of the overlap heat exchanger joint can be carried out in a single stage. When the heat exchangers are connected between the tubes, the tube and shell test pressures should be carried out after overlapping assembly.
Related Industry Knowledge
- Characteristics of shell and tube h...
- Structure of air cooler
- The structure of the APV plate type...
- The introduction of plate heat exch...
- The structure classification of pla...
- Positioning system of heat exchange...
- Matters needing attention in heat e...
- The scope of application of Alfa La...
- Performance of compressor
- What Is A Heat Exchanger Gasket
- How to Disassemble Plate Heat Excha...
- Plate&frame heat exchanger cleaning
- Types of corrosion in heat exchanger
- Heat exchanger corrosion protection
- What factors affect heat exchanger ...
- Titanium heat exchanger advantages
- What is plate heat exchangers
- Plate heat exchanger efficiency
- Plate heat exchanger passivation
- Plate& Frame Heat Exchanger Gaskets...