WTSML Heat Transfer Technology Co.,Ltd
Add: Qiaoxing Road 150, Torch Industrial Zone, Licheng Area, Quanzhou, Fujian, China
Tel:86 595 22168106
Fax:86 595 22142090
Heat Exchanger Plate Type Selection
Heat transfer plate type or corrugated type should be based on the actual needs of heat transfer occasions. We should use a small resistance PHE plate type for big flow rate and small allowable plate heat exchanger pressure drop. On the contrary,Used the big resistance heat exchanger plate design.
Determined to choose a plate type exchanger or brazed plate heat exchanger depend on the fluid pressure and temperature.Don’t choose small heat transfer area per plate when confirm the heat transfer plate type.It cause too much gasket plate,lower velocity between two plates and low heat transfer coefficient.We should pay attention to this problem if the plate exchanger calculation is large.
Plate & Frame Heat Exchangers Flow Path and Channel Selection
The flow refers to a set of parallel flow paths in the same flow direction of a medium in the plate exchange.The channel refers to the fluid flow channel between two plate heat exchanger plates in PHE. Generally, several flow paths are connected in parallel or in series to form different combinations of cold and hot medium passes.
The path combination should be based on heat transfer and fluid resistance to calculate and meet the requirements of process. As far as possible to make convective heat transfer coefficient equal or close in the cold and hot channel.So it can get the best heat transfer effect. It will obtain a large heat transfer coefficient value when the heat transfer coefficient on both sides is equal or close. Although velocity between two plates in plate type heat exchanger design is different,the average flow rate is still calculated in the heat transfer and fluid resistance calculation.It’s easy to disassemble because the connections are fixed on the compress plate for “U” shape single pass.
Plate Type Exchanger Pressure Drop Check
In the plate type heat exchanger design selection,Usually pressure drop has certain requirements, so it should be checked. If the pressure drop exceeds the allowable pressure drop, plate type heat exchanger design calculation must be repeated until met the process requirements.
Plate Heat Exchanger Calculation Method
The heat transfer coefficient and the pressure drop is calculated from the performance curve of each plate heat exchanger manufacturer's product.Generally the performance curve (criterion correlation) comes from product performance testing. If plate heat exchanger types is lacking in performance testing, it can get the criterion correlation through the reference size method, according to the characteristics of plate-type geometric size.Some of the international heat exchanger design software are used this method.
Plate Heat Exchanger Selection Software
On the heat exchanger selection software, general manufacturers has own heat exchanger software according to their own plate type cooler .International heat exchanger design software is HTRI, HTFS and so on. General plate heat exchanger calculation software is seldom aired in public.You can refer to some software which is showed in the website.
Related Industry Knowledge
- Characteristics of shell and tube h...
- Structure of air cooler
- The structure of the APV plate type...
- The introduction of plate heat exch...
- The structure classification of pla...
- Positioning system of heat exchange...
- Matters needing attention in heat e...
- The scope of application of Alfa La...
- Performance of compressor
- What Is A Heat Exchanger Gasket
- How To Size Plate Heat Exchanger
- Why Plate Heat Exchanger Used
- How To Design Plate Type Heat Excha...
- How To Clean Plate Type Heat Exchanger
- How To Install Plate Heat Exchanger
- Plate Heat Exchanger Gasket Replace...
- What Is A Heat Exchanger Plate
- How Does Heat Exchanger Plate Work
- How Does A Plate To Plate Heat Exch...
- Where To Use Plate Heat Exchanger