WTSML Heat Transfer Technology Co.,Ltd
Add: Qiaoxing Road 150, Torch Industrial Zone, Licheng Area, Quanzhou, Fujian, China
Tel:86 595 22168106
Fax:86 595 22142090
Glueless or glue free gaskets are provided for the most plate heat exchanger model,These heat gaskets are replaced as follows
1.Peel the old plate heat exchanger gasket from the PHE plate and make sure that all parts are completely removed.Note that there is not scratches in the PHE gaskets groove when disassembling.
2.Wipe the plate cooler gasket with a clean cloth or cotton yarn mop to ensure that there is no foreign materials remain that could cause the plate gasket to seat improperly.
3.Secure the new rubber gasket to the PHE plate by gasket clip at the edge of the plate heat exchanger plates. Note that there are two gasket tags at each attachment position at regular intervals around the circumference of the heat exchanger plate.
4.Ensure that all the channel plate gasketsclips are are in proper position before closing the plate coolers.
5.The plate type heat exchanger is closed and tightened with the gaskets providing a tight sealing
Previous: Heat Exchanger Gasket Production Process
Next: No Information
- High Flux Heat Exchanger Technology
- Structure Of Shell And Tube Heat Ex...
- Introduction Of Air Cooler
- The Characteristics Of APV Plate He...
- Type Plate Heat Exchanger Gasket
- Gasket Structure Characteristics
- Heat Exchanger Plate Sealing Principle
- Classification Of Heat Exchanger Ap...
- The Characteristics Of Alfa Laval P...
- The Application Scope Of SONDEX Hea...
- Heat Exchanger Gasket Production Pr...
- Development Of Plate HHeat Exchanger
- Plate Heat Exchanger Price
- Plate Heat Exchanger Heat Loss